Hello. I just joined this forum and found that I am having same open ground problem with my Reliable inverter in off grid house. Besides disconnecting blue wire from chassis, what other steps are required? House panel has neutral and ground on same bar which is earth grounded. Cable running from inverter to house receptacle is a 30 amp RV plug. Any help would be greatly appreciated. Thank you!